Here you will find several detailed case studies related to Kompozit'all UK heating and ventilation products:
Project Length: 2 days
Completed by: Toast
Isle of Wight Council office - Isle of Wight
Toast had to investigate and survey a 25 metre flue at the Isle of Wight council offices. The flue serviced 2x large commercial condensing boilers. The flue was leaking badly through the chimney walls due to the amount condensate caused by the boilers.
Reconstructing the flue
3 metres had to be reconstructed to the chimney and a 28M 450mm FuranFlex25 Black was installed using 2 FuranFlex steamers. Due to the stack size we were able to winch the FuranFlex25 into position and maintain cross sectional area. New stainless steel pipework was installed from the boilers to the FuranFlex which now has a suitable valve for collecting and draining the condensate.